Finally, the pump controls will be tested by simulating a "pump-up" condition and "stop-pump" command at the end of the control cables.
Many thanks to Jack for his expertise and donated labor in correcting that problem.Our new system will be monitored closely to assure that the system is behaving as required.9/1 begin pumping water into the Andy Creek water distribution system and our 15,000 gallon steel tank.We are no longer using any water from the Forest Service well and redwood storage tank.The valves that allow water from the Forest Service from our new well, only.
Online dating kostenlos vergleich Herne
The controller and relay appears to be working properly, but a series of further tests will be made to verify that it is operating consistently.Also, the Franklin Pump-Saver electronics need to be programmed to protect our pump from "no-water" and rapid-cycling conditions before the pump is put into operation.After starting our system about three weeks ago for the first time, we experienced a minor "glitch".Our 15,000 gallon water tank was empty due to the failure of our new submersible pump to pump water.While this was occuring, all of the new valves and threaded connections were checked for leaks at the connection point of our new 3" high-density polyethylene pipe with the 4" PVC pipe. Also checked was the 2" brass pipe and valves in our new pump house.
- Singlebörse österreich Paderborn
- Mann kennenlernen frau
- Dating seite gratis Heilbronn
- Internet dating Oberhausen
- Hildesheim singlebörse
- Flirt chat kostenlos Stuttgart
One small leak was encountered....which should be very easy to seal. Next on the to-do list is completing the control wire splices and testing those splices for continuity.
The problem was discovered by Akland Pump to be the "Pump-Saver" component of the control system. This equipment is designed to shut down the system automatically until it has been programmed and electronically synchronized with our pump.
The Pump-Saver is designed to protect the pump from damage due to low water in the well, over/underload, over/under voltage, and rapid cycling conditions.
6, as well as cleaning up the pipe excavation areas, re-seeding the soil covering those excavations with native grasses.
Control-wire splice boxes have been installed over two of the buried junction boxes as additional protection.